Inspections and Testing to be performed
by D & L Quality Painting, Inc.
A. Air temperature thermometer (0 degree F to 120 degree
B. Surface temperature (0 degree F to 250 degree F minimum)
C. Sling psychrometer (30 degree F to 110 degree F or continuous
D. Pictorial surface preparation standards (SSPC-Vis. 1)
E. Surface profile comparator (Test-Tex replica tape with
micrometer minimum requirement)
F. Magnifier (5X)
H. Wet film thickness gauge (.05 to 20 mils requirement)
I. Magnetic dry film thickness gauge (Type 1 magnetic pull-off
gauge minimum requirement)
A. Confirm the blast quality by comparing the blasted surface
using a surface profile comparator (Test-Tex replica tape
with micrometer minimum requirement)
B. Conduct regular equipment inspections per shift to maintain
oil and water separations
C. Inspect all blasted surfaces before applications of coating.
D. Visually check for flash rusting. If rusting is detected,
surfaces shall be reblasted until no rusting is apparent
A. Check each coating material shipment for acceptable condition
of the containers and packages. Insure manufacture date does
not extend beyond shelf life.
B. Check spray equipment daily for correct air pressure,
cleanliness of agitators, hoses, and p along with correct
size of tips and air caps.
C. Check continuously coating mix proportions and agitators
and that specified pot life limitations are not exceeded.
D. Check dry film thickness
on steel with elcometer or mikrotest thickness gauge in Accordance
with (SSPC PA2)